350W 300W 500W 600W 700W MPPT Solar PV Grid Tie Micro Inverter GMI series Input 18V-50V DC Output 110V-240V 65
300W/350W Grid Tie inverter is a compact unit,which directly converts direct current into alternating current for powering appliances and/or office equipments and connecting to utility grid.The AC output from Smart Micro inverter is synchronized and in-phase with the utility grid.
On Grid Tie Inversor
Rated Output Power:280W/320W
DC Input: 18V-50V
AC Output Voltage: 120V/240V
Frequency Range: 50/60HZ Auto
MPPT range: 24V – 40V.
Solar Panel Voltage: Vmp30-39V; Voc38-46V
Solar Panel Power: maximum 300W/350W
On Grid inverter Certification:CE
• Use solar panel ONLY connect to this equipment.
• This equipment is ON-GRID Microinverter, To make it work properly, it must be connected to the power grid correctly,and the power grid is working properly, When the power grid stopped working, it will also stop generating.
• Do NOT exceed PV panel(s) voltage over the Solar Grid Tie Inverter max input voltage.（Voc＜50V）
• Do NOT exceed PV panel(s) power over the Grid Tie solar Inverter max input power.（300W/350W）
• The positive and negative poles of the solar panel cannot be reversed. If you extend the solar panel cable. You need to be careful about this problem.
• Install away from direct sunlight and direct rain exposure.(Ventilated, dry, cool)
The 18-50V grid tie micro inverter will start up at 24V, after starting, the Solar Microinverters can work in 18V-39V (Vmp).Solar Panel Voc cannot be higher than 50V.
Vmp = solar panel working voltage; Voc = solar panel open circuit voltage.So don’t think that 50V is the working voltage (Vmp)
Why not use 12V solar panels? 12V panel working voltage Vmp18-20V, open circuit voltage Voc20-24V.
the 12V panel is just a starting voltage. If the sunlight is weak, the working voltage will be lower than 18V. It is easy to make the Solar micro-inverters work unstable, and the inverter will start repeatedly. It is easy to damage the Smart Microinverter.
Recommended Solar Panel Voltage: Vmp30-39V; Voc38-46V
1.Green light steady=Microinverter in generating.
2.Red flash=Microinverter in waiting.
3.Red light steady
c.Over/low AC voltage protection.
d.Over/low DC voltage protection.
e.Over/low AC frequency protection.
1XGrid Tie Inverter
1 x AC Cable 30CM
1 x English User's Manaul